My call went to the office about noon and the problem was diagnosed and fixed by 6:30! Saved me from a cold night.
Extremely knowledgeable, trustworthy and kind, I wouldn't call anyone else!
Ken is very personable and knowledgeable. We felt we got exactly what we wanted at a reasonable price.
Ken is always professional and courteous, and very proficient! Always great service!
Jill has been great over the phone with scheduling, answering questions, and follow up. Keith was very professional, knowledgable, and kind. He included us on the process when necessary, and walked us through it all in the end.
I've used knight heating for years, great people, always great service and the perfect epitomie of an American Family owned business.
I appreciate the efficiency, honesty and reasonable price. Thank you Ken
Knight did a great job on our furnace tune up. On time, friendly and knowledgable.
So glad we called someone certified to work on a Trane furnace. He qas quick, efficient, and found the problem that no one else could! Thank you!!!
Professional, interactive, knowledgable service.
Repeat customer for sure!
Installed new Trane high efficient furnace and Bradford white power vented water heater.
Free estimate on a new Trane central air
Installation of a new Trane xr13 13 seer central air
Installed new high efficient Trane xr16 air conditioner
Replaced capacitor on a goodman air conditioner and tested operation
Little giant condensate pump failed and leaked water all over the floor, replaced pump and tested operation.
Another Bryant capacitor
Replaced capacitor on a Bryant air conditioner
Installation of Trane xr14 central air
Real tough call, furnace switch was turned off accidentally, turned switch on and it works now!
Installation of a new Trane xr13 central air
Free estimate on a new furnace and air conditioner
Free Trane furnace and air conditioner estimate
Free estimate on a new Trane air conditioner
Ac clean and check
Replaced capacitor on an icp condensing unit in otsego
Goodman air conditioner in elk river not starting, replaced capacitor.
Bryant not running, capacitor failed, replaced and tested.
Another blown capacitor this time on a luxaire air conditioner
Goodman air conditioner not working, found blown capacitor and fan motor shut down on hi limit. Replaced capacitor and cooled down the motor with water. Running good now
Carrier air conditioner in new hope won't start. Found blown out capacitor, replaced part and tested operation.
Customer installed their own thermostat and cooling wasn't working, found thermostat not properly seated, secured and tested operation.
Added r22 to a system that wasn't cooling well
Estimate on new Trane air conditioner
Removed bird from inducer motor on Lennox furnace